Consult Keston Boilers ‘s entire C45 C40P C55 C55P catalogue on ArchiExpo. Page: 1/ 88, E, Main Control Box (C55/C55P/C45). , E, Control Panel. 73, E, Combustion Blower. , Gas Valve / Venturi Ass. (C45/C55). Keston C55, tips, tricks, advice and notes. READ THE DANGERS SECTION. The idea of this is so you get an idea of your boiler, so you know if your engineer is.
|Published (Last):||9 October 2010|
|PDF File Size:||10.9 Mb|
|ePub File Size:||12.49 Mb|
|Price:||Free* [*Free Regsitration Required]|
The top of the heat exchanger – same deal – try not to wreck the insulation, and dont drop crud into burner or heat exchanger.
Although suitable for open vented systems with combined feed and vent arrangements, the C45, C40P and C55 P are low water content boilers. Keston Boilers Ltd declare that there are no substances harmful to health within the appliance or used during the production of the appliance. No lights on display board and fan running flat out is the classic sign of this.
Who are Boiler Guide Boiler Guide is the smarter way to find heating engineers in your area. Table of Contents Add to my manuals Add. Fan kewton — boiler cannot detect fan rotation.
C45 C40P C55 C55P – Keston Boilers – PDF Catalogs | Documentation | Brochures
List Of Contents 0. The heat will hide a lot of drips! Check both flow and return sensors are located on the correct pipes and are producing the correct readings.
Optional Accessories Chapter 1: The C45 and C55 boilers can be fitted in compartments with very small clearances required around the appliance refer to Section 1. What work do you require? It has its place, pound for pound it gives the most output you can get, and it can be fitted into incredibly difficult places. By pressing ‘print’ button you will print only current page.
Keston Boiler Error Codes
Condensate trap – the orange pipe on the bottom of this pic shows the pipe to the condensate trap – this is a common blockage spot Boiler Keston Qudos 28s User, Installation And Servicing Instructions Fan powered high efficiency modulating domestic condensing gas system boiler 67 pages. Adjustments – min gas is under the star drive cap – where the governer is, Max gas is the screw brass above it down the aluminium tube.
Keston have mounted into a auto close widget. Page 47 WD Chapter 7: Page 16 9 ft at the top of the boiler.
Keston C45 Installation And Servicing Instructions
Exchanging A Boiler It is essential that sludge or scale is removed from an existing system. Flue – this is now attempt three to resolve this issue – originaly the flue tube was a corrugated rubber effort, reinforced with wire, which was actualy better than version two, a degraded one shown here, which was a smooth rubber tube, now we have a stainless item with rubber ends, if the latest one is any better time will tell – we all thought version 2 was fine This is the flue overheat stat – see the central little red button – press to reset.
Possible heat exchanger fault. Summary of Contents for Keston C45 Page 1: I do not advise this as it compromises the boilers ‘room sealed’ status Condensate Drainage WD Chapter 3: The unit automatically adjusts gas and air rate according to demand to give an output in the range of Ok, so as usual the pictures are a bit naff, but I hope it helps.
The boiler will turn off when the flow temperature exceeds 10 The C45, C40P and C55 P feature an integral pump exercise function which will run the pump, without firing the boiler, for 10 seconds in the event the boiler is on standby for in excess of 24 hours without firing. FYI – this one is knackered – it has a hole.
Lets first start by NOT complaining about this boiler. This is the low water pressure switch Air Intake Connection